|Contact Us For Quotation
MEWOI3800N Built-in Grounding Resistance Online Tester,Online earth resistance tester,GEO Meter
MEWOI3800N Non-contact Earth Resistance On-line Monitor is high-tech product that our company has devoted to "grounding resistance detection technology research" for more than ten years, specialize for online monitoring grounding down lead connection status, circuit grounding resistance and metal circuit connection resistance. On-line testing, non-contact measurement, grounding wire pass through the perforation of the detector, definitely will not influence grounding effective for lightening and normal operation, no need the self-inspection, real time on-line testing. Provide RS485 wire communication (support MODBUS-RTU communication protocol) , The monitor is composed of sensor and PCB module, which is suitable for user secondary development integration.
MEWOI3800N Non-contact Earth Resistance On-line Monitor suitable for transmission line tower grounding; Meteorological lightning protection grounding; Petrochemical grounding; Communication grounding; Substation grounding; Railway facilities grounding; Construction warehouse grounding; Metal circuit resistance; Electrical equipment grounding and others place. It can also be used for anti-theft monitoring of grounding wires and metal cables.
MEWOI3800N Non-contact Earth Resistance On-line Monitor can install and use singly, and also can set up wired or wireless network system.
■ PCB Module
■ Connection Wire
■ Warranty card/Qualification card
■ Paper Box
|Loop circuit grounding resistance on-line monitoring, metal return circuit resistance connection online monitoring, grounding condition monitoring. anti-theft monitoring of grounding wires and metal cables
|Detector：6VDC～9VDC，50mA Max(external power supply).
|Sensor Perforation Size
|Test data>100Ω, communication send “OLΩ” command
|J1：Signal output, power input interface
|J2：Sensor and PCB interface
|P+:Power input with positive R+：Signal output with positive
|P-：Power input ground R-: Signal output with negative
|GND：Signal ground, short connect with power input ground (P-)
|I+、I-Current coil interface U+、U-Voltage coil interface
|1pcs ,0.5 meter length(5 core wire)
| Line Wire
|1pcs ,1 meter length(5 core wire)
|Red---power supply input anode;
|Black--- power supply input cathode;
|Green---RS485 signal anode;
|Yellow---RS485 signal cathode;
|White--- grounding wire shield
|(power supply input cathode can connects with analog grounding by short circuit connection)
|RS485 communication protocol(support MODBUS)
|GPRS communication (optional)
|Working Temperature And Humidity
|Grounding lead Interference Current
|Should be avoid
|External Magnetic Field
|External Electric Field
|Single Measurement time
|About 0.5 second
|The ground wire goes through the center hole of the sensor
|PCB should install into other protective case
Wired Network System (Self -Development Software)
Wired network system through RS485 communication protocol to transmit data, build up by the detector, 【communicator, monitoring software, power adapter, computer (above equipment need the user provide and secondary development) 】and so on, suitable for short-distance 1500 meters grounding resistance monitoring.
Wireless Network System (Self -Development Software)
Wireless network system through GPRS communication protocol to transmit data ,build up by the detector(built-in GPRS transceiver module), 【SIM communication card, monitoring software, power adapter, computer(above equipment need the user provide and secondary development)】 and other components for long-distance ground resistance monitoring., distance is not limited.
Principle & Application
MEWOI3800N Non-contact Earth Resistance On-line Monitor, the basic principle of measuring the grounding resistance is to measure the loop resistance. Firstly sensor send out a drive pulse signal to the measured ground return circuit, then measured ground return circuit responses a pulse electromotive force E, under the influence of electromotive force E will generate current I in the be measured ground return circuit. Sensor measures E and I value, and gets resistance value of be measured ground return circuit through the formula: R=E/I.
Loop Resistance & Metal Loop Connection Resistance Tesing
Loop resistance is a composite value includes A point grounding resistance value, grounding down lead metallic conductor’s resistance value, metal overhead line’s resistance value, connection resistance value (contact resistance) between grounding down lead and metal overhead line, B point grounding resistance value.
If grounding network A and grounding network B up and down are connected together on the ground, Detector measures out the resistance value of metal return circuit is very small in general situation, only few of and less than one Ohm, this is the metal loop connection resistance, as a equipotential resistance, but not grounding resistance. Therefore the detector is much convenient to test metal return circuit connection resistance.
Single point grounding system: If between grounding network A and grounding network B haven`t overhead line, and not connect together on the ground, then grounding network A and grounding network B can regard as standalone single point grounding connection. Detector cannot test the grounding resistance of single point grounding system directly, will display “OL” overload symbol. Therefore it needs adding one or more auxiliary grounding electrode, to form multipoint loop circuit.
Three point grounding system: In the following figure, the tested ground pole is A and the other two auxiliary ground pole is B and C. The poles A, B, C are connected together on the ground. In the three ground poles grounding down leads were installed on a detector, can accurately test the ground point A resistance value.
Calculated as follows:
Sensor: 1 pc; PCB module: 1 pcs; Connection cable: 1 piece